|Originally posted by Tony Kania:|
The standard will be county and state codes.
Here is a link to Cedar Rapids Building Codes. In here will be your answer. If not, call them directly. They will answer your code related questions... http://www.cedar-rapids.org...and_trades/codes.php
This is all I can find in the link you provided to the Electrical codes
"34.50 – BONDING OF GAS PIPING
Gas piping systems shall be bonded in accordance to the manufacturer's installation
requirements. The bonding jumper shall not be smaller than #6 AWG copper wire or
And this is all I can find in the plumbing codes of the links:
5.36 - 1210.15.5 ELECTRICAL BONDING OF CORRUGATED STAINLESS STEEL GAS SYSTEMS.
Section 1210.15.5 Electrical bonding of corrugated stainless steel gas systems is added as follows:
1210.15.5 Electrical bonding of corrugated stainless steel gas systems. Alternative CSST bonding may be approved by the mechanical inspector when such alternative design meets manufacturer requirements and International Code Council - Evaluation Service (ICC-ES) product certification system verification or International Association of Plumbing and Mechanical Officials - Evaluation Service (IAPMO-ES) [see also 310.1. 1 of the Fuel Gas Code for an alternative design].
Neither seem to answer my question.